Take a sneak peek at the new NIST.gov and let us know what you think!
(Please note: some content may not be complete on the beta site.).
NIST Authors in Bold
|Author(s):||Sunil Lee; David A. Yashar; Piotr A. Domanski;|
|Title:||Performance Improvement of a Roof Top Air-Conditioning Unit by Refrigerant Circuitry Optimization|
|Published:||January 26, 2013|
|Abstract:||In this experiment-aided simulation study, we achieved the performance improvement of a Roof Top Unit (RTU) by optimizing an evaporator‰s refrigerant circuitry using evolutionary algorithms. The system used in this study was a 2-stage 7.5 Ton RTU with an air to refrigerant finned-tube evaporator consisting of 144 rifled tubes divided amongst 16 circuits. The RTU was designed to operate as an air-to-air heat pump, but was modified with water-cooled condensers for the purpose of testing. Performance tests were conducted in a conditioned environmental chamber in line with AHRI standard 340/360 (2007) by maintaining the liquid line saturation temperature and subcooling from the manufacturer‰s test data by adjusting the condenser water flow rate and temperature. We measured the capacity of the original design included in the RTU to be 26.4 kW (90100 Btuhr-1). We also measured the in-situ air velocity profile under test conditions using Particle Image Velocimetry (PIV), a non-intrusive, laser-based technique. The results of the PIV measurements uncovered several non-uniformities in the air velocity profile due to the blower location, the condensation drip tray, the placement of the air filter racks, and the position and orientation of the heat exchanger within the unit. The measurements showed that the range of air velocities passing through the heat exchanger varied from 0.5 ms-1 (1.64 fts-1) to 3.0 ms-1(9.84 fts-1), with the integrated average of the measurements being 1.75 ms-1(5.74 fts-1). We simulated the performance of the original evaporator operating with the measured air velocity profile using NIST‰s heat exchanger program, EVAP-COND. We matched the simulation results to the measured data by selecting appropriate correction factors for the refrigerant heat transfer coefficient, refrigerant pressure drop, and air-side heat transfer coefficient. We then used this model to optimize the evaporator circuitry using the evolutionary algorithm based module|
|Proceedings:||2013 ASHRAE Winter Conference in Dallas|
|Dates:||January 26-30, 2013|
|Keywords:||Air conditioning unit, evaporator, refrigerant circuitry optimization|
|Research Areas:||Energy, Building Equipment Efficiency|